› PLCGurus.NET Live & Interactive Forum › PLC Questions and Answers › Rockwell, Allen-Bradley, Stratix › Powerflex 755 ethernet control using Compact Logix › Reply To: Powerflex 755 ethernet control using Compact Logix
Hi Rob and welcome to the forums. I believe its parameter 877 that needs to be set to Port 13 Reference. This tells the drive it’s getting its commands from the embedded Ethernet port. After that you should be able to make use of the I/O words in your logic.