- This topic has 0 replies, 1 voice, and was last updated 1 month, 1 week ago by Jim Manley.
- December 17, 2021 at 6:27 pm #20382Jim ManleyModeratorKarma: 262Rank: Jedi
I have a bunch of PowerFlex 525 VFDs with the 25-COMM-E2P boards installed in them. The controls network is connected to the E2P ports in the drives. When I browse the I/O configuration list for the network in Logix 5000 Designer, all the VFDs are listed. If I double click on a VFD, Logic 5000 will display the Module Properties page. All the tabs on the module properties page will display except the “Drive” tab. For some of the drives, I get an “Automatic Connection Failed” error messages. For others, I get the Drive page that lets me access drive parameters, etc. (same functions that can be done in CCW).
I have used CCW to download and compare all the parameters for a drive that gives me the connection error and one that doesn’t. I have compared all the network related parameters and can’t find anything different between the drives.
When I compared the “Port Configuration” tab in Logix 5000 I found that the drives that give me the connection fail error DO NOT have the IP Address/Subnet Mask/Gateway Address parameters set and the “Obtain IP settings automatically using DHCP” radio button is selected. The drives that allow me to access the Drive functions have the IP address data properly configured and the “Manually configure IP settings” radio button selected.
Is it correct that the IP configuration displayed in the Module Properties is a part of the .ACD file that is loaded into the controller?
Update: I was checking all the drives to see which ones needed to be edited in the .ACD file when I found a drive that has the proper IP address but an incorrect subnet mask. This drive also gives me a connection failure error. I’m assuming the incorrect subnet mask is causing the problem.
- You must be logged in to reply to this topic.