Implementing Stratix 5700 NAT
In this article we will be implementing Layer 2 NAT with Layer 3 routing as shown in the the network topology depicted below. For this example we will be leveraging two Allen-Bradley Stratix 5700 Managed Industrial Ethernet switches (Full Software Version) and three Logix based controllers (machines). With Stratix 5700 NAT capability configured, we can setup a NAT instance per VLAN. When we create multiple VLANs on one Stratix 5700 switch we can connect multiple identical machines and leverage Layer 3 routing to route between the various VLANs.
Stratix 5700 Router Configuration
If you’ve not seen our article showing you how to initiate the Express Setup mode on a Stratix 5700 switch, you can view it here before proceeding. Also, we have created an in-depth article and video tutorial on how to effectively configure and implement Inter-VLAN Routing on a Stratix 5700 switch here. Both of these articles and video tutorials are highly recommended before proceeding with this article as we build upon and rely heavily on those foundations.
The first thing we’ll need to do is perform an Express Setup on the first Stratix 5700 switch. Once in the Express Setup mode of the Device Manager, assign an IP address to your router and enable the routing functionality on the switch. This has all been covered in explicit detail in our Stratix 5700 Inter-VLAN Routing article.
Configure your router with the following IP address assignment, we can continue on to configuring the necessary VLANs needed to implement our network design.
To implement our network we will need 2 VLANs for the 2 identical machines (Machine 20 and 21). One VLAN for the Line Controller and the default VLAN for the management of the switches.
Enable the routing capabilities of the Stratix 5700 by going to Admin and then select SDM-Template. Select Lanbase Routing and press Submit. The switch will reload with the SDM -Template for routing.
Go to the Routing page to Enable Routing between VLANs and press Submit.
In our network example above the line controller and the PC are connected to the router. That means that we have to set the
Smartports and the correct VLANs on these two ports.
- Line controllers is connected to Fa1/1.
- PC is connected to Fa1/16
- Nat Switch is connected to Gi1/1
With this information select the proper Smartports on the router.
The PC is connected to VLAN1, no changes needed here. The Line controller is connected to VLAN20 so we need to change the VLAN number for port Fa1/1 from the default to VLAN10.
Go to page Configure
The configuration of the router is finished.
At this time we can check if the routing is working by pinging the line Controller. Connect the Line controller to Port Fa1/1 on VLAN10 and your PC to Port Fa1/16.
Ping from your PC to the IP address of Line Controller 172.16.10.10. If it doesn’t work check your settings again.
Stratix 5700 NAT Configuration
Perform the Express Setup now on the second Stratix 5700 NAT switch.
Notice we have the gateway for the default VLAN configured in this Stratix 5700 NAT switch to allow it to communicate with other VLANs.
Now similar to what we did in the router we need to configure all the VLANs needed on the Stratix 5700 NAT Switch.
Now configure all the Smartport on your Stratix 5700 NAT Switch.
Go to page Configure and then Port Settings. Change the VLAN number for the ports as shown.
The last step is to create the NAT instances for the different machines. Go to Configure and select NAT. Create a new instance and do the same as in the screenshots below. Do the same VLAN configurations for both Gi1/1 and Gi1/2. This means that you can use both ports to connect your switch to the upper network.
Press Submit to save the configuration.
At this point you should be able to ping the Line Controller and both Machine 20 and Machine 21 from your PC as shown.
Want to see this complete article in action? Watch it Now!
I certainly hope you’ve enjoyed this article and I do encourage you to become a member of our growing community of professional engineers, technicians and technologists, Register Here!
Also, check out our YouTube Channel to see some great videos…and don’t forget to like and subscribe to our channel!
If you enjoyed this article be sure to check out some of these good reads too:
- How To Become A PLC Programmer
- Difference Between DCS And PLC
- How Much Does A PLC Programmer Make
- PLC Versus Microcontroller – What’s In Your Plant?
- Essential Tools Every PLC Programmer Needs
- How To Implement A ControlLogix PID Controller
Lastly, if you run into any problems in your day-to-day engineering activities please be sure to check out our Live and Interactive PLC Forum!
And if you so desire, assist other community members by replying or offering helpful information to the questions or challenges they may be facing right now!
Hi! Fred here, I am the founding member and site moderator here at PLCGurus.NET. I’d like to be the first to welcome you to the site. I have over 20 years in the Industrial Automation and Control Systems field. Be sure to Register Today!